Synchroscope E1505 shield (E 1505, E-1505, E1505, e1505, e 1505, e-1505) analog E155 (E 155, E-155, E155, e155, e 155, e-155)
Synchroscope E1505 is designed to synchronize the three-phase generator. Used in mobile power plants.
Synchroscope E1505 used in ambient temperatures from -40 º C to +50 ° C and relative humidity up to 100% (at 90 ° C) for inclusion in the network for a maximum of 15 minutes. Intervals of 30 minutes. Performance E1505 (E155) conventional and tropical.
Measurement range, rated voltage and how to enable the device synchroscope E1505:
Basic error (deflection from the mark synchronization) of ± 3 °. Position upright.
Power consumption of the generator operating at rated voltage 127V and 380V devices is 1.5 W at 220 V - 2.5 W power generator connected at voltage 127V and 380V is 3x1, 5W, with 220 - 3x2, 7W.
Mark on the scale marked synchronization.
Changing readings synchroscope E1505 caused deviation of ambient temperature (up to class H) does not exceed ± 0,9 ° arc. for every 10 º; under the influence of external magnetic field strength of 400 A / m - not exceed ± 1,2 ° arc., when the instrument is on a ferromagnetic shield is less than ± 0,2 ° arc.
E1505 Weight - 1.9 kg.
Dimensions of additional devices such as R1820 / 5 - 155h127h95mm, weight 1.1 kg. The device is built into the body of e tsya e proof design, suitable for flush mounting on a vertical panel. The device has a round steel housing with die-cast metal cal square flange with a plastic cap.